Buy Gefran PID Temperature Controller, 96 x 48 (1/8 DIN)mm, 2 Output Relay, V ac, V ac Supply Voltage ON/OFF RR Browse our. setting up the Gefran controller for the application referenced above. Additional software and hardware configuration information can be found in the User’s. Gefran controllers are built with SMT technology. The instrument provides a complete operator interface, protected by a Lexan® membrane that ensures.
|Published (Last):||11 July 2010|
|PDF File Size:||3.70 Mb|
|ePub File Size:||20.15 Mb|
|Price:||Free* [*Free Regsitration Required]|
Lexan that guarantees IP65 level protection.
In addition to the control and alarm outputs, you can also have outputs that repeat the state of the digital or retransmission input by process variable, setpoint, deviation, alarm trip points and values acquired via serial line.
Gefran Customer Care Service is contacted for assistance with any problems. Got it, continue to print.
R Digital from serial line Absolute Def. Navigating through the controller menu. The instrument is supplied with an “EASY” configuration calling for just a few parameters only those pertaining to the model ordered and essential to the controller’s operation.
Page 21 [ gfg ] c. Configuration Fourth menu to set up This menu makes it possible to configure various control parameters. The Gefran is a high performance configurable controller, widely used in industry for processes involving transmitters 4…20mA, 0…10V and temperature sensors.
Documentation – Previous versions. Maximum number of outputs: A second auxiliary analog input from current transformer is available. Navigating through the Controller Menu Keep pressed down to gefan through the menus in sequence and release it when the required menu appears.
Alarm 1 Alarm 2 Alarm 3 AL. It does not engage if the oscillations drop below 1.
GEFRAN INSTRUCTIONS FOR USE MANUAL Pdf Download.
Enter text from picture: Temperature Controller gefran User Manual Single display temperature controller with universal input 13 pages. Comments to this Manuals Your Name. N disabled disabled disabled enabled gerfan disabled Select number gefrn enabled alarms disabled enabled disabled enabled enabled gefan disabled disabled enabled enabled disabled enabled disabled enabled enabled enabled enabled enabled By adding the following figures to the value in the table it is possible to enable a series of supplementary functions: Page 25 0VT Output settings Second menu to set up This menu makes it possible 100 configure the parameters of the Controller outputs.
Heat-Cool Control Application example: This manual also for: In particular, this new line of Gefran tempera- and linear thermocouples, supplied with current and ture controllers is the ideal solution for application voltage with accuracy better than 0. Page 22 This menu makes it possible to configure the various parameters that control serial communication between the controller and the supervisor.
Cencal Memory Map – Summary of Contents for gefran Page 1: It is therefore an essential requirement for programming and configuring the controllers correctly.
For even simpler configuration, you can use a PC programming kit consisting of a cable and a guided program for Windows environment. The purpose of a temperature control loop is to 12200 the process temperature accurately at a determined level.
S Minimum limit of main input scale Min During the test, all the display segments and the 7 indicator lights will flash. An additional output 24VDC, 30mA max. Catalogue Click here for advanced filter options. Don’t have an account?
Gefran 1200 Instructions For Use Manual
It continuously reads system oscillations, immediately seeking the PID parameter values that reduce the current oscillation. The instrument’s entire programming procedure is made easier by grouping the parameters in function blocks CFG for control parameters, Inp for inputs, Out for outputs, etc. Manual Tuning If the Integral Time value is too long Weak integral actiondeviation between the controlled variable and the set- point may persist.
Maintenance When it is switched on again a self- illegible diagnostic test is performed that checks intermittent start up of all the segments displays the value Below is a list of tags that have been applied to this product. Page 12200 Configuration Fourth menu to set up This menu makes it possible to configure various control parameters.
With scale settable in limits: LEDs will flash when softstart or autotuning are in progress or when a sensor fault occurs Trigger pre-configured control gefrran alarm reset, Auto Manual mode… via remote switch. Max value associated with the input selected with the TYP parameter Ki.
Output Virtual instrument outputs S. Instrument identification code [